The incinerator will have chimney, castable top quality refractory cellular lining as well as burner shell, perforated blind for the main as well as additional combustion chambers and air blood circulation system.
The burner shall likewise have the following:-.
– Ash door.
– Primary as well as secondary heaters and also fans.
– Temperature level indication gadgets.
– Electrical circuitry from the neighborhood isolator.
– FD fan.
– Air receiver.
– Air ductwork complete with air dampers.
– Pressure as well as temperature level assesses.
– Fully wired control panel
The bulk oil storage tank shall have a capacity of 10,200 litres as well as be put at 0.5 m above ground on a firm concrete cradle, total with the following:-.
– Drain pipeline.
– Air vent pipe.
– Oil level sign.
– Gain access to ladder to the top of the storage tank.
– Finishing of the container with a minimum of 2No. layers of bituminous paint.
– Manhole cover total with a gasket.
– Dip stick.
– Any type of various other essential device.
The daily oil tank of capacity 1,800 litres as well as dimension 1220x1220x1220mm pressed steel tank high shall be placed 2.5 metres high above finished floor level on a steel stand, strongly secured on the ground and also the steel participants to be bolted. The everyday oil container shall have an oil degree indicator, accessibility manhole, washout, overflow, inlet as well as outlets connections and gateway valves.
The adjoining pipeline of 50mm size between both storage tanks will be class ‘C’ black mild steel pipe, complete with a 50mm diameter filter. The burner fuel supply pipe from the day-to-day container will be a 25mm size class ‘C’ black mild steel.
The adhering to will additionally be supplied.
– 25mm diameter fire valve.
– 25mm size high capacity strainer.
– home heating faucet along the heater supply pipe, 25mm size
The heater supply pipe will have 25mm thick fiber glass insulation and do with gauge 20SWG galvanised steel sheet.
The tenderer will give all the required controls for appropriate safety and also acceptable working of the installment.
The heater shall be suitable for 35 sec redwood No. 1 scale fuel oil. It will be robust in building and construction and be produced in actors iron or other appropriate products full with placing plates. It needs to be quickly mountable and also demountable for convenience of cleansing and upkeep. The heater shall have an appropriate supply of oil which will easily stir up as well as burn in a secure way. Sufficient provision will be offered to prevent any solid matter in the oil, or any type of issue that may divide out from the oil from harming any parts or chocking of any kind of orifices or shutoffs. The complimentary filtering system location ought to be sufficient to make sure that the filter does not need dismantling for cleaning up more often than annually. The burner will have fire guidance by photo-electric cell with concurrent sequence controller for automated start up, running and shut-down of the burner.
The burner shall have all the essential controls e.g.Solenoid shutoffs, ignition controls, image electrical cell gas safety and security controls, low stress fuel supply cut-off etc.
The heater will satisfy BS 799: part 3 as well as 6 1981 or any other pertinent British standard.The burner shall be as NU-WAY models or equivalent and also accepted.
The incinerator shall operate in an automatic manner with all the required controls. These controls are to include security elements such as fire failing unit, pilot lights, integrates, beginners, overload contactors, ON as well as OFF switches for heaters and also followers, combustion chamber temperature signs for primary and also second chambers etc.
i) Electric ignition button ‘ON’ prior to the oil is supplied.
ii) Delayed return to re-start setting to permit purging.
iii) Re-start after temporary electrical supply failing.
iv) Favorable safety and security lock-out in instance of flame failing from whatever reason.
v) Red signal light on control board to indicate safety and security shut out.
vi) Image electric protective cell as fire failing tool.
The controls shall be mounted on appropriate control panel to be mounted in a position easy to review and manage from the charging door side of the incinerator.
The control board will be produced from anodized, 16SWG, light steel sheet.
HICLOVER is growing brand for environmental protection field, and market share with most of Africa, Middle East, Southeast Asia countries and part of North America, Europe territory. We are trusted partner for governmental organizations, non-profit organizations, international contractors, logistics organizations, military, pet cremation business owners, etc. We have export experience more than 40 countries, including war zone like Iraq, Afghanistan, Somalia, South Sudan. Mobile: +86-13813931455(WhatsApp) Website: www.hiclover.com Email: email@example.com Email: firstname.lastname@example.org